Payment & Shipping Terms:
|Voltage:||127V/230V||Current:||5(30)A, 10(60)A, 20(100)A|
|Measurement:||Active Energy||Type:||Static Single Phase Electric Meter|
1P Static Single Phase Electric Meter KWH Measurement Meter High Accuracy Power Meter
Functions and Features:
＊ Front board three fixed installation;
＊ 5+1 digits display (99999.9 kWh) by step motor and pulse machinery counter;
＊ Standard configuration one port of pulse output passive (polarity). Distant impulse output passive (no polarity) is also acceptable. It can contact with all kind of AMR system conveniently, complying with standard IEC 62053-31;
＊ Five LED respectively instructions every power state and signal of closed power impulse and distant power impulse ;
＊ Single direction single components measure single phase two wire active power consumption. It is nothing with direction of the trend of load current. Complying with standard IEC 62053-21;
＊ Directly connection in 2 types;
＊ Extended terminal cover, in order to protect to use electricity safely.
|Model||Accuracy||Rated Voltage (V)||Rated Current (A)||Starting Current (A)||Insulation Performance|
|AC voltage 4kV for 1 minute, 1.2/50us wave from impulse voltage 6kV.
Model DDS155 single phase energy meter is a kind of new style single phase two wire active energy meter, it adopt micro-electronics technique, and imported large scale integrate circuit, using advanced technique of digital and SMT techniques, etc.
The meter meets relevant technical requirements of class 1 single phase active energy meter stipulated in international standard IEC 62053-21.It can accurately and directly measure 50Hz or 60Hz active energy consumption from single phase AC electricity net, it is used indoor or outdoor, and display total energy consumption by step and motor type impulse register.
With following features such as: good reliability, small volume, light weight, specious nice appearance, convenient installation, and etc, the meter is widely used in any occasions.
＊ Use only isolated tools.
＊ Do not connect the meter to a 3 phase - 415V AC - network.
＊ Place the meter only in dry surroundings.
＊ Make sure the used wires are suitable for the max current the meter can measure.
＊ Make sure the AC wires are installed correctly before activating the current/voltage.
＊ Do not touch the meter connecting clamps directly with your bare hands, with metal, blank wire or other material as you will have the chance of an electricity shock and a possible chance for health damage.
＊ Make sure the protection cover is placed after installation and has been sealed.
Why Choose Us
1. Professional manufacturer for more than 15 years.
2. Highly experienced production team in RADARKING factory work-shop.
3. QC Systerm: Quality controlled on all production lines, and QC inspectors work independently from the production line.
4. Good quality production with quick delivery.
5. Accepted OEM/ODM.
6. Accepted small MOQ.
7. Factory certification: ISO9001, 14000, STS