Payment & Shipping Terms:
|Multiple Protection:||Lightning Strike, Surge Protection||Maximum Impact Current:||20kA Or Higher|
|Limit Voltage:||≤500V Or Lower||Product Model:||RDK-IP08M16|
IEC Flat Plug Electrical Distribution Unit,
AC220V Electrical Distribution Unit,
Electrical Distribution Unit , Flat Plug Power Strip for Power Supply
Power Distribution Unit(PDU) is the power distribution socket for cabinets, it is a product designed to provide power distribution for cabinet-mounted electrical equipment. It has various series specifications with different functions, different installation methods and different socket combinations, and can provide suitable rack-mounted power distribution solutions for different power environments. The application of PDU can make the power distribution in the cabinet more clean, reliable, safe, professional and beautiful, and make the maintenance of the power supply in the cabinet more convenient and reliable.
|Input||Rated input voltage||AC220V 50/60 Hz|
|Max load current||16A|
|Power supply type||Single phase input, National standard C20 socket|
|Input parameter collection||Current, voltage, active energy, power (active power, reactive power, apparent power, power factor)|
|Output||Output socket||Eight circuit; National standard 10A socket|
|Rated output voltage||AC220V 50/60 Hz|
|Rated output current||10A|
|Output parameter collection||Current, power, power factor|
|Display||LCD||Backlit text LCD display|
|Port parameter||RJ45(NET)||10/100M, Ethernet access interface|
|Cascade port||2 RS485 ports for equipment cascade (photoelectric isolation)|
|Sensor port||2 temperature and humidity sensor interfaces|
2 LCD display up/down buttons
1 LCD display down button
One is used as a restart and reset button, single press the device to restart;Long press is the reset function, the device parameters are restored to factory settings.
|Dimension||Black 19 inch 1U chassis||485mm X 250mm X 44mm|
The front of the device
The back of the device
Device panel description:
Device system initialization
After the device is powered on, the LCD display is initialized and enters the normal working state after completion.
Detect the load current of each output unit of the PDU. If the load current of a certain output unit exceeds the threshold setting, the device will alarm.
If the total load current exceeds the threshold setting, it will automatically jump to the current interface and the total current value will flash.
If the temperature/humidity exceeds the limit value, it will automatically jump to the current interface, and the temperature/humidity value will flash.
Set up one HOST and the others as slaves. Up to 255 devices can be cascaded, including 256 devices in total.
Connect one end of the accessory cascading cable to the OUT interface of the HOST, and one end to the IN interface of the slave, and then use a cascading cable to connect the OUT interface of the current slave to the IN interface of the next slave, and connect each slave in turn .
Industrial automation control power management
1. Automatic control of factory power
2. Automatic control of traffic power
3. Automatic control of lighting advertising power
4. Automatic control of power supply in the burning room
5. Automatic control of air conditioner power supply
Data center power management
1. Enterprise Computer Center
2. IDC network data center
3. Financial Computer Center
4. School Computer Center
5. Telecom Computer Center
6. Government Computer Center
7. Military Unit Computer Center
Contact Person: Mrs. Ada Yang