Payment & Shipping Terms:
|Name:||Three Phase Electric Meter||Min Current:||3*5(60)A|
|Rated Frequency:||50Hz/60Hz||Life Span:||10 Years|
|Terminal:||Terminal Connected||Standard:||IEC62053-21; IEC62052-11; IEC62053-23|
LCD Display Three Phase Electric Meter 3P Watt Hour Energy Meter Pulse Output
DTS150 is a three phase electric energy meter for automatic meter reading that conforms to the requirement of IEC62051 Standard for Class 1.0 and 2.0 Static AC Active Energy Meter; The meter adopts the advanced SMT technique to design, manufacture to measure the active 50Hz or 60Hz active energy consumption from three phase four wire AC electricity net; The meter is used for setting indoor or setting out door directly, and this meter has LCD displays showing the active energy consumption for easily reading by the workers, it has the following features: phase failure indicator, RS485 communication, remote power off /on and remote alarm and so on.
Comprising Table of Model And Impulse Constant (the specification constant value is subject to the nameplate)
|Normal Operating Voltage||3×230V/400V|
|Limit Operating Voltage||1.2Un|
Voltage Circuit Consumption
Current Circuit Consumption
|Normal Operating Temperature||-35~+80 ℃|
|Limited Operating Temperature||-40~+85℃|
|Storage And Transportation Temperature||-40~+85℃|
|Storage And Operating Humidity||≤85%H|
1. The meter shall be installed in the dry area with good ventilation condition to ensure safety and reliability during installation and operation. If the meter shall be installed in the area with dirty and easily gets damaged, the metering box should be configured to protect meter against the dirty environments.
2. The dimension of meter is as below: the holes should be digged ahead accord with the size and the the meter bottom should be fixed on the strong, fire-proof subjects.
＊ Use only isolated tools.
＊ Place the meter only in dry surroundings.
＊ Make sure the used wires are suitable for the max current the meter can measure.
＊ Make sure the AC wires are installed correctly before activating the current/voltage.
＊ Do not touch the meter connecting clamps directly with your bare hands, with metal, blank wire or other material as you will have the chance of an electricity shock and a possible chance for health damage.
＊ Make sure the protection cover is placed after installation and has been sealed.
＊ Installation, maintenance and repair should only be done by a certified electrician.
＊ Never break the seals or open the front cover as this might influence the functionality of the meter.
＊ Do not through, drop, kick or other physical violence to the meter as there are high precision components inside that will break or make the meter measure inaccurate.
＊ Do not mount the meter in area's with harm gas, dust, mildew or insects or on unstable surfaces.