Payment & Shipping Terms:
|Installation:||Direct Connected||Communication:||Wifi/GPRS/RS485/Carrier Communication Module|
|Smart Meter:||Electricity/Water/Gas Meter||Type:||RDK-CJQ Data Collector|
1. Product Description
Data Collector with RS485 interface for Smart Electricity Meter Power Grid System can support LV concentrator to complete the data communication channel switching for the smart energy meter of RS-485 communication method, guide rail mounted and compactable with hook mounted design, suitable for the applications where the meter box space is limited and requires only transparent data transmission.
|1||Operating Frequency Band||470MHz~510MHz / 223~ 230MHz||Or Customized|
|2||Modulation||GFSK / GMSK||Configurable|
|3||Air Transmission Rate||Default 10Kbps, 1.2Kbps~100Kbps||Or Customized|
|4||ERP||< 17dBm / 20dBm~30dBm|
|6||Signal Level Range||3.3V / TTL Level / CMOS compatible|
|7||Air Baud Rate||Default 10Kbps, 1.2Kbps~100Kbps||Or Customized|
|8||Supply Voltage||220V AC -20%~+20% 50Hz,1.9times Standard voltage, no damage within 4 hours|
|9||Working Current||Transmit Current≤100mA;Quiescent Current≤50mA|
|10||Serial Interface||Data Bits 8;Even Parity Check, stop bit 1|
|11||Software Maintenance||Wireless Smart Update|
|12||Bit Error Rate||Less than 1%|
|13||Size||Meet the China State Grid Regulation issued in May, 2013||Or Customized|
|14||Technical Regulation||Meet the China State Grid Regulation issued in May, 2013||Or Customized|
3. Technical Parameters:
1, Operating Power: AC220V±20%,50Hz(single Phase)
2,Static Power Consumption: ≤5W
3,Upward Communication Interface: Radio Frequency ≥300m (open field)
4,Downward Communication Interface: RS-485 bus line. M-BUS bus line, Radio frequency.
5,Operating Temperature: -25℃～＋55℃
6,Relative Humidity: 5％～95％ (non-condensate)
4. Installation Requirements:
4.1.1 Wall mounted, has three fixed holes, can be fixed on the wall surface.
4.1.2 Collector should be installed in the building, if outdoor installation, should configure the outdoor protective box, in avoid the direct sunlight and rain.
4.1.3 Collector should be installed the at the position which the meter is relatively concentrated.
4.1.4 The power supply of collector should be stable, in avoid the data can’t be collect caused by the power outage. The power line adopts the 2×0.5mm2 thickness or thicker wires, and install the earth-leakage protective device.
4.2.1 The antenna will be installed at the outdoor or outdoor relative open position, and antenna is towards the concentrator.
4.2.2 The antenna will be within the scope of effective protection of lighting rod and will be more than 1.5 m below than lighting rod.
4.2.3 Install the corresponding frequency antenna according to the antenna terminal instruction on the collector case. Must guarantee the upward and downward antenna communication frequency, channel, concentrator, smart meter correspond strictly when installation. The communication frequency of sucker antenna will be checked the label at the bottom of antenna.
4.2.4 Antenna bracket fixed well, and the antenna base will be fixed firmly on the bracket. Tight the magnet part of antenna head, and also tight firmly the junction between the antenna and collector.
4.2.5 In order to avoid the antenna was surrounded by the metal objects. The antenna position should be far away from the air conditioner compressor, transformer, communication cable,etc.